View Full Version : Ch Valve Now Working ,Tip!!!!
04-27-2006, 07:53 AM
I wrote a few days ago about a faulty check valve not keeping the pressure and the pump not working on an irrigation system.I thought maybe it was dirty so I took the my compressor I use for fall blowouts and pumped 150 psi into the check valve through the removable cap. I had to reprime the pump but now it is working perfectly. Certainly easier than changing the valve,just passing it along ...Walt<>
04-27-2006, 05:55 PM
Obviously, a check valve needs to seal tight, but a leaky check valve won't prevent a pump from priming and working. If there is a restriction in the suction line, like from a clogged well point, the air pressure can help clear the inlet screen, and make a driven well functional again. Water pressure works, too.
vBulletin® v3.8.6, Copyright ©2000-2015, Jelsoft Enterprises Ltd.