Originally Posted by Fireguy97
That RP doesn't have an air gap. The Relief Port is below the flood plain. That wouldn't pass up here either.
The powers that be, won't care as long as nothing happens. If and when it does happen and lawyers get involved, there will be a crap storm dragging everyone that touched that 'assembly' in with it.
I was wondering how long it would take for someone to observe that the photo showed an RPZ in a meter pit.
That install is very much a matter of presiding local standards. It happens that there is a clause in the regional code that provides for such installs, with the requirement that the actual flood plain in the region is below the device. They do not highlight that clause, but it is there.