Thank you Bernie! Yes, that is the one I was referring to. 12g wire required if your transformer has a 25a breaker. I didn't get all the details exactly right. But I knew I heard something like that.
I figure it's just safer to do use 12g or greater anyway.....
That's another one I need to keep in mind - use conduit if we go under sidewalks!
Thanks for correcting me on these items.
Anything else discussed in that meeting? Other NEC rules we need to keep in mind?
Last edited by JimLewis; 03-02-2013 at 01:29 PM.