Originally Posted by gusbuster
What we see in the picture, is that even to local water code?
Here, CA code says and assuming that it's 12" above highest head that it supposed to be attached to a non ferrous metal (ie. copper, galvanized,brass)
Back on topic
Man you guys are hard on this guy. We're here to learn right?
Same here , no PVC before backflow.