It's time to revise best lv lighting installation and maintenance practices to address LED systems. Let's put our heads together on this one. Unique LED system characteristics that may not apply to incandescent installations: Extreme long life - wiring and splices must maintain integrity for at least 20 years Wider range of acceptable voltages. Possible presence of unintended RF interference. Different failure modes for LED's compared to incandescents. Possible elements of new best-practice recommendations: Splices to be soldered and sealed with shrink-wrap; or other equally corrosion-resistant connection used. Use of tin-coated wire should be considered. Daisy-Chains, T-Methods, or multiple hubs may be used. Splices should, however, be kept to a minimum. Deeper trenching and conduits should be considered - given the extended period of system use (and the possibility that the homeowner will not pay for proper maintenance). While there may be the temptation to use one or two wire runs for an entire system, there is some wisdom in using more wire runs in case a single home run wire is damaged. Using multiple wire runs greatly simplifies troubleshooting and prevents the entire system from going out at once. Maintenance should include periodic cleaning of the LED device (especially if retrofit LED lamps are used). Accumulations of dirt and debris may degrade the LED and impair thermal transfer. The installer would ideally have a footcandle/color meter to measure LED performance at time of installation. This would be used as a reference for future claims of luminance and color degradation. The installer would ideally have a RF detection meter to ensure that LED devices do not interfere with household transmitters/receivers.