Update. Was able to make it out there to continue work. Owner had more pressing things for me to do. I jumped the BF from the meter to the main line, also skipping MV. Still weak pressure. Even isolated to just one zone, same result. Found the main control valve, it was filled with water. Bailed and bailed, could not find a primary shut off for the irrigation meter. No leaks, Turn the meter on and off a few times to make sure it was open all the way, checked the static pressure, 80 psi. Whats left for to do is check flow pressure and have city come out and check their meter and to see if they can find the tap, off the main to the irrigation meter. Am I missing anything else? Thank You everyone.