Hey no shame in that. And I'm not annoyed don't worry about that. So the only concern I have about your setup is that 1" is too small I think and I think you'll have way too much friction loss. But as a rule of thumb I never have an outlet larger than my inlet. The last thing you want is to pump water faster than your pump can suck in. That leads to cavitation and burned up pumps. If possible I would maybe increase the inlet size to 1.5 so that you can run your 1.25 pipe successfully. With that distance and elevation rise you should plan for around 8-10 psi loss at the highest head if you use 1.25 the whole way. That's a very high ball park estimate not knowing how many heads on a zone.