I looked at a job today that had get this. 9 20 watt halogen pathlights powered by a multi transformer all on one homerun. they wired it this way. Daisy chain with 8 gauge on the 14 volt output. The first fixture about 5 feet from the transformer and the next 4 about 15 feet on center then there was a space of about 50' before the next 4 fixtures were again daisy chained and 15 feet on center all on the same cable run. Obviously the first fixture or so was constantly blowing it's lamp/s. The second set of fixtures was significantly voltage dropped. How do these guys get hired?