Separate names with a comma.
Discussion in 'Landscape Lighting' started by pete scalia, Sep 30, 2007.
how bout this for a hub system
quality! i wish i knew that technique
Is that OSHA approved???
Wow! Apparently box fill was not a concern there. Try getting a blank cover on that thing. I'm not so sure about OSHA, but the code inspector would have a field day with that mess.
What? Pete, they weren't using romex for 12 volt application were they?
I thought I'd post this photo to show the range of my lighting talent.
That picture looks like an electrical supply house threw up!
dont laugh... SamIV and I found something similar to that on a 30k hanover outdoor line voltage system we removed. Total mess... some fixtures had zero volts.. some had 110 and some were shorted and getting 208.